13 Simple C17 Thermostat Wiring Diagram Ideas
Related photos in this diagram:
Other recommended diagram ideas:
C17 Thermostat Wiring Diagram - Hello.. At the pinnacle you are saying it could additionally cope with cooling hundreds.. Does that imply i will switch it from iciness to summer season mode without difficulty while bloodless water runs thru the ground in preference to hot water ? How is cooling mode started out then ? Many thank you.
Sure, that would be the easiest way. The opposite manner, if for a few reason you need to use the 24v one, is to get a small 220->24v transformer or a comparable power supply (like for a computer). But, for the reason that actuator attracts handiest 1w, a 60w computer power deliver is overkill. The thermostat may be configured to paintings in no (heating) or nc (cooling) mode. To wire a 230v actuator you want to attach the two wires to n1 and l1 on the thermostat.
Properly capture, i should've remembered some different thermostat that did this or assumed the "air" icon become associated. It doesn't appear to be this unit has this mode. It would nonetheless be a fairly smooth conversion: a relay with ac coil input and nc contacts (inclusive of az2280-1b-240af or az2280-1c-240af). Join the output of the thermostat (l1, n1) to the relay input and the normally-closed contacts (of the relay) in collection with the cooling power deliver. You can then have a spdt transfer that switches the thermostat l1 output among the cooling answer above and the present heating solution. It sounds extra complex than it certainly is.
See my respond beneath. It has a relay, so it connects each a neutral at one pin and line (section) at the alternative, while brought about on. You may try and avoid some other relay via connecting one terminal to neutral, however no longer sure if your device/load permits that. Now not sure about the sensor, haven't tried it. However if the cord is of desirable high-quality, you can likely add to it without issues. The sensor is 20k, so i doubt an amazing cord beneath 50 meters can reach values in that variety.
It depends on what voltage is on that wires and what they can receive. If they're floating (with respect to line voltage) and that they require that a contact closes, you can attempt connecting n and n1 to them.