13 Practical Can, Use 12 Gauge Wire With A 30, Breaker Images
Related photos in this diagram:
Other recommended diagram ideas:
Practical Can, Use 12 Gauge Wire With A 30, Breaker Images - It feels like you may be incorrect as to how this is wired, or that perhaps i'm just now not know-how your explanation. As others have noted, it is not feasible to get 240 volts from a unmarried pole in a one hundred twenty/240v break up segment device. Each tandem breaker affords 2 120 v circuits, this is authentic. However, in case you degree between the terminals on a unmarried tandem breaker, you will get zero volts. This is because the terminals are each powered from the same leg, and so are at the equal voltage capacity. If you degree from a terminal at the top tandem breaker to a terminal on the bottom one, then you'll degree 240 volts. That is because each breaker is connected to a exclusive leg, which can be each one half of of a 240 volt circuit. Murray bus backplane with interleaved palms so adjacent full size breakers are on opposite legs. No longer real for the mh-t mp3030 breaker pair, each breaker inside the set is 1/2-width and the combination is fed off only one leg blade.
In particular, there are murray mh-t 30-amp breakers. These are tandem breakers and not "slimline" or "skinny" breakers -- the 2 breaker switches on every are not connected in any manner. This type of breakers is used for the clothes dryer and the opposite for an electric water heater. I inherited a first-rate panel box from a home owner that wasn't continually fond of assembly the desired nec codes. As such, there are some oddities inside the panel. One such oddity is the reality that he mounted more than one tandem circuit breakers to be used in 120/240 circuits.
What is wrong -- the foremost protection issue right here is that with a circuit fault, only one of the breakers inside the set may additionally experience, leaving the 240v circuit in part energized. For example if the dryer heating coil burns thru and one quit touches ground, that aspect will trip, leaving the other leg hot. You definitely need a circuit fault to completely strength down each legs. Additionally associated is the reality that anyone no longer taking note of the panel setup may additionally strength off the circuit to work on it and now not comprehend they switched off adjacent pairs in preference to change pairs of each 240v circuit, leaving a hot leg in the circuit they suppose is powered down. You want things to be fail-secure. This isn't always fail-safe, however is a booby entice watching for the inattentive or moved quickly. Nec frowns heavily on things like this.