11 Practical Wire Gauge, 100, Breaker Collections
Related photos in this diagram:
Other recommended diagram ideas:
11 Practical Wire Gauge, 100, Breaker Collections - Appearances to me are the diagram on the field does now not match the real panel, as the panel has 20 breaker spots (as i examine it) whilst the diagram suggests 14. And sure, i realise it's missing a main breaker, so i included the alternative two pieces i understand discover the max amp load; the conduit and the meter.
In case you do now not have a massive house and you in general have non-electric powered home equipment (including herbal fuel), then 125 a is plenty. But, it looks as if you do not presently have sufficient loose spaces within the breaker panel for a new two-pole breaker for the a/c.
The pinnacle double pole breakers are earlier than the "primary" disconnect, which means that they will always have energy whilst the wires feeding the panel have energy. I am guessing there is a disconnect beforehand of this panel, maybe at the meter or as a standalone disconnect. Based on their size, i'm guessing one (50a) is for an electric powered stove, electric powered heater, or maybe a subpanel. The opposite (30a) is in all likelihood for a dryer, water heater, subpanel, or some different equipment.
It's very usualary|traditional|regular|normal|typical|standard|common
When i run the cord alongside the ground joist, does it need to be secured to the joist or can it simply cling there and relaxation on the drop ceiling? Looks like it should be secured to the joist with wire hanger or some thing.
Now here's the trouble: fellow comes over and says i have a one hundred fifty amp panel and there is room (which i can see) for a couple greater breakers on it, and gives me a extensively higher ac quote (3500 for a lennox three ton 14 seer, all of the same bells and whistles).